Technical description of multi-bags filter vessel in factory
Multi-Round Liquid Bag Housings effectively remove dirt,pipe
scale,and other contaminants from process liquids.Quality
construction and design assure clean effluent and protection for
all down stream equipment.
multi-bags filter vessel in factory Operation
Unfiltered liquid enters the housing above the filter bags or
strainer baskets,fills the interior of the housing and continues
through the bag or strainer basket.Solids are trapped inside the
filter bags or strainers and easily removed when the housing is
serviced.Our standard O-ring seal between the baskets and the
housing ensures a positive seal to prevent bypass.
Features of multi-bags filter vessel factory
1 Max flow rates up to 540ton/h
2 Two basket to 18 basket housing designs,depending upon the
required surface area and volume of fluid to be filtered.
4. Low pressure drop
5 Swing bolts with bearing-assisted davit closure
6 EPDM,Viton,Buna seals-lid and basket
7 Differential,drain,and vent port.
8 SUS304 or 316L strainer basket.
9Accept #2-size filter bags.
Working Principle of multi-bags filter vessel factory
Bag filter is a new filtration system, filter bag supported within
the metal basket, the liquid flows into the inlet,
filtered through the bag out from the exit, impurities were
intercepted in the bag, the bag after the replacementcan continue
The bag filters is through the filter bag, in the effects of
stress, through the filter bag, be prefiltration filter bag
interception down pollutants
stranded in the filter bag,filter bag phosphate contained residue
stay inside, and
filtrate along metal bearing a basket with netting on top wall
outflow, achieve the purpose of filter.
Operation instructions of multi-bags filter vessel factory
Simple operation, it just required that qualified micron filter bag
be installed in the filter basket strainer, check working condition
of the O shape sealing ring , then tighten the ring bolt of filter
cover to start working. After pump is started, the pressure gauge
will slightly rise, initial pressure is around 0.05Mpa,as the
working time increases, the residue inside the filter housing will
increase gradually, when pressure raches 0.4Mpa, the filter must be
stopped working and operator should open the filter cover to check
the residue in the bag, replaceable filter bag could be continue
used (generally,washed bag filters could be repeated use). It is
appropriate that filter pressure be setted at 0.1-0.3Mpa , but it
could be adjusted through the return line or return valve on pump
,it is important that high working pressure will damage the filter
bag and protection strainer.
Application of multi-bags filter vessel factory
1. As the security department of the NF,UF,RO,EDI systerms;
2. Biopharmaceutical,petrochemical,chemical industry,etc.
3. Electronics, microelectronics, semiconductor industries using
high pure water filtration;